Click here to view prior versions of this section.
B105.2 Buildings other than one and two – family dwellings. The minimum fire flow and flow duration for buildings other than one-and two-family dwellings shall be a specified in IFC Table B105.1.
Exception: A reduction in required fire flow of up to 75 percent, as approved, is allowed when the building is provided with an approved automatic sprinkler system installed in accordance with Section 903.3.1.1 or 903.3.1.2 or the International Fire Code.
(Ord. M-4138 §24, 2015; Ord. M-3957 §17, 2010; Ord. M-3659 §1, 2004)